Click here to send Ron a pdf document for publication on this Topic
Documents must be less than 200k in pdf format
Topic: lighting rcd,s
Mar 09 2018 16:01
I am upgrading the lighting circuits in an old villa.The lights are wired inside steel conduits which will be removed and the cables terminated/removed and replaced with new TPS.Do I need to replace the MCB with a rcd? or does it count as a direct replacement and no rcd required?Or is it a new circuit which requires a rcd? It is not an extension so 188.8.131.52 exception 2 will not apply
Mar 09 2018 16:17
It's not a new subcircuit so 184.108.40.206 does not apply. Its either simple replacement (ESC) or replacement-plus-alteration (CoC + ESC); and the clause that does apply is 220.127.116.11. Neither para of that clause calls for an RCD for lighting, so no need to worry about Exceptions. In fact Exception 2 never applies; nor does the lighting bit of Exception 1. they were (wrongly) carried-over from a previous set of RCD rules.